Which Recessed Escutcheon?
I have run into this issue many times in the last few years. What recessed escutcheons can be used with what pendent sprinklers? The short and most correct answer is: Recessed sprinklers are listed for use with a specific escutcheon. i.e., Order the recessed escutcheon form the same manufacturer as the pendent sprinkler. All the manufacturers indicate that recessed sprinklers are to be ordered as a unit, even though most ship the escutcheons separately.
The reason this is such an issue is the number of independent suppliers of fire protection products who sell recessed escutcheons. I know a lot of fire sprinkler companies keep these generic escutcheons on the shelves and use them with what ever pendent sprinkler they got the best price on that week. It eliminates an inventory headache and helps reduce costs. But what is their liability?
After a lot of checking on the web I found only one manufacturer of escutcheons which was UL listed. ARGCO is UL listed File EX4170 and their product data states :
There is no possibility of a sprinkler head failure due to ARGCO escutcheons. It is no longer a warranty issue, since UL announced, “Installed properly, the product cannot affect sprinkler head operation.”
So while the possible liability of installing pendent sprinklers with generic escutcheons might be small, It would seem prudent to at least use a manufacturer such as ARGCO which provides a UL listing and would stand behind their product.
I for one, however, will continue to specify and order escutcheons from the same manufacturer.
Part 1 – The Beginnings, Perforated Piping Systems
The forerunners of the automatic sprinkler system were the perforated pipe and open sprinkler. The perforated pipe system, as its name implies, was simply a series of small perforated pipes attached to the ceiling and divided into sections.
In 1806 John Carey filed a patent in London for a perforated pipe concept for fire protection systems, but the system never gained acceptance. The world’s first recognizable sprinkler system was installed in the Theatre Royal, Drury Lane in the United Kingdom in 1812 The apparatus consisted of a cylindrical airtight reservoir of 400 hogsheads fed by a 10 inch water main which branched to all parts of the theater. A series of smaller pipes feed from the distribution pipe were pierced with a series of ½” holes.
From 1852 to 1885, perforated pipe systems were used in textile mills throughout New England as a means of fire protection. The Providence Steam and Gas Pipe Company, later to become the Grinnell Company, was a major installer of these systems.
James B Francis was one of the first to develop a system of perforated pipes and his system was installed many New England mills. Other systems were the Whiting system, Hall system and Grinnell system. Each system having a different spacing ,and sizes of holes in an attempt to effectively distribute the water. The Hall system is notable in that it used galvanized sheet metal piping. It was soon removed from service as unreliable.
These early systems did establish some basic design concepts, Such as spacing of lines, and sizing of the pipes. One early rule was that the sizes of the pipes were of such size that the area of the orifices would not exceed 50 per cent of the area of the pipe that fed them.
Frederick Grinnell’s first patent, on March 12, 1878, concerned perforated “sprinkling-tube” that had the holes bushed with a non-corrodible material such as brass. This indicates that potential clogging of the perforations due to oxidation of the iron pipe was a major problem.
The success of perforated sprinkler piping was short lived. It is evident that with this system there was a great waste of water, and probably poor distribution. Furthermore, the systems were not in any way automatic. They were manually activated by the building occupants. By discharging water over the entire area of the room where there was no fire, the water damage usually greatly exceeded the fire damage. The lack of automatic operation was the main problem as nearly all of the highly destructive fires occurred at night when there was no one in attendance.
Foreign Fire Sprinklers
A Guest Post Submitted By Mike W
Have you ever wondered about the use of fire sprinklers outside the U.S.? There are actually many countries that use and manufacture sprinkler heads. The use of sprinklers now spans the entire globe. Sprinklers can be found on every continent with Antarctica being a possible exception. However, sprinklers are not manufactured on every continent.
I have been collecting sprinkler heads for a little over six years, but I have recently gained a special interest in sprinklers from other countries. In January of 2009, I purchased my first foreign-made sprinkler heads. My first foreign heads were from England and Denmark. While Denmark is host to one manufacturer, “GW”, England is home to the most sprinkler companies outside of the U.S. These brands include: Mather & Platt (Grinnell), Atlas, Matthew Hall, Spraysafe, Wormald (British sector), Titan, Firekil, and Angus. Continue reading
In the beginning there was brass and it was good. Brass while a good metal for use in water, is was not suitable for corrosive atmospheres found in some industrial facilities.
I live near the coast in Florida and have seen many sprinklers installed in areas such as parking garages, apartment breeze ways, etc. All a nice shade of green. My company makes good money replacing heads in places such as this. Early on in the sprinkler industry they discovered this and worked to develop finishes and coating to protect against corrosion.